الحمد لله والصلاة والسلام على رسول الله وعلى آله وصحبه أجمعين EQUIPMENT DETAILS Main Fire Pumps SCHEDULE OF PLANNED PREVENTIVE MAINTENANCE Work Plan EQUIPMENT DETAILS Main Fire Pumps صيانة دورية جداول جاهزة مضخات الحريق الرئيسة مضخة Capacity Qty: Lot Make & Model Location Main Fire Pumps Consumable Spare Parts Task Description W / Weekly M / Monthly Q / Quarterly SA/ Semi/Annually A/ Annually SST / Seasonal Start/Up SSH / Season Shut Down 2W M 3M 6M A Notes Item Description Qty Notes Check for any leakage and repair Check the pump head at nominal flow and at 150 % or nominal flow to ensure conformity with design requirement. Check for the relief valve calibration by gradually closing the test line Check pressure switch setting for automatic cut – in and cut-of jockey pump Grease and oil the bearing Check power is healthy on panel and clean Check bearing and mechanical seal Clean and paint. Make general cleaning , check impeller, clean housing Check seals and change if necessary Check the motor full load current by manipulating the flow Inspect unit for unusual noise and/or vibration, ensure that it is in good working order. Provide lubrication, if necessary. If unit is not running or an identified problem requires the unit to be serviced, perform ALL Non-Critical Tasks listed below Flush and clean strainers. Check operation of gauges and record pressures and temperatures. Inspect seals and packing, tighten or replace as necessary. Lubricate impeller shaft bearings. Inspect motor and pump alignment. Other recommended tasks Inspect mounting bolts and vibration isolators of the pump under load conditions. Start and stop pump, noting any vibration and overall performance. Inspect drive shaft coupling. Notes Use additional sheets if required PPM routines based on Complete Running hour where recommended by the Manufacturer http://www.sitei.net/up/do.php?id=45 في أمان الله !